HVAC Company - Trussville, AL
Comfort Now Heating & Air Conditioning LLC proudly serves Trussville and surrounding areas. We service most any brand equipment on the market. Whether you are installing a new system, changing out a piece of equipment, or just needing basic service on your system we can help. We will work with you to find the right solution to your comfort needs. Unlike some companies out there we are not here to upsell you on anything that you do not need. We will make repairs first.
Cody came out to my house on a Saturday when my heat quit working. He looked at my system and found that the blower motor was bad. He told me that a new motor was more than a new furnace with warranty would be. He was looking out for my best intrest. I would definitely recommend him and his company.
It was great. The man who came out really knew what he was doing. Our heat works great now.
This was the best experience I have ever had with an HVAC company. Showed up on time, reasonable and fair price, courteous and professional. You can't go wrong using this company.
315 Forest Dr
Trussville, AL 35173
|Village Lane Condensor Unit
Installed new 3 ton Goodman heat pump condenser unit. Repaired electrical whip to unit, Repaired low voltage wiring to unit, Replaced 10amp fuse in air handler, Seal taped air handler duct connections, Hauled off old equipment, Checked temperatures (54 supply / 72 Return), Filed warranty. Charged system with 9lbs of R-22 Refrigerant.
|Forest Drive Furnace
Installed new Goodman furnace in crawlspace and removed old furnace.
|Meadowbrook Gas Pack
Installed a new 3 ton Goodman gas package unit on rental house. Removed old unit.
|Roebuck Drive Repair
Replaced 35/5 440VAC run capacitor. Added 1 lbs. of R-22 refrigerant to system. Charged to a 13 degree SH. Replaced run capacitor, Taped up two return ducts that had come apart under the house, Checked temps and voltages.
|King James Repair
HVAC not blowing cool air. Checked unit and repaired burnt compressor wire going to the run capacitor. Unit was cooling properly with 68 degrees registering at the kitchen vents upon completion.
|King James Circle Precision Tune-Up
Serviced HVAC system, Check for leaks, Cleaned outdoor coil, Checked indoor coil (good) Replaced 2 20X20 filters, Checked voltages and capacitor. Added 4 lbs of R-22 Refrigerant to system
|1st St Precision Tune-Up
Performed a precision tune-up on the air conditioning system. Cleaned outdoor coil, Checked temperatures and refrigerant charge, Checked voltages, Inspected indoor coil, Re-taped indoor coil, Repaired condensation drain line that was pouring water into basement. Thawed unit out and added 2lbs of R-22
Center Point, AL
|Roebuck Drive Precision Tune-Up
Serviced HVAC System, Cleaned condenser unit coil, Checked wiring connections and tightened, Checked refrigerant charge, Checked voltages, Evaluated system - Noted below: Checked furnace under house and noted several items that needed to be addressed.
|Cameron Drive Repair
Installed two new evaporator coils, replaced two damaged air handler cabinet doors, replaced two line sets, charged both systems, replaced two condensate drain lines and pump, sealed existing duct, and serviced three systems.